netxml-ups(8)

NAME
netxml-ups - Driver for MGE Network Management Card / Proxy (XML/HTTP Protocol) equipment

NOTE
This man page only documents the hardware-specific features of the netxml-ups driver. For information about the core driver, see nutupsdrv(8).

SUPPORTED HARDWARE
netxml-ups support all recent MGE models which use a Network Management Card or Proxy (MGE XML/HTTP protocol based). This applies to both MGE Office Protection Systems and to MGE UPS SYSTEMS. Supported card and proxy models are:
    NMC Minislot (Ref 66102),
    SNMP/Web Minislot card (Ref 66244)
    NMC Transverse (Ref 66074),
    NMC & Modbus/JBus (Ref 66103),
    Network Management Proxy. Older models, such as SNMP card (Ref 66062 and Ref 66045), use the SNMP protocol and should use the snmp-ups driver with the "mibs=mge" parameter.

EXTRA ARGUMENTS
This driver supports the following optional settings in the ups.conf(5):

timeout=value
    The timeout for connecting to and reading from the UPS. Defaults to 5 seconds. Don't change this value unless you know exactly what you're doing. This value must never be higher than half the MAXAGE value specified in upsd.conf(5), otherwise you risk that upsd(8) declares the driver stale while it is waiting for a connection to timeout.

login=value
    Set the login value for authenticated mode. This feature also needs the password argument, and allows value settings in the card. This feature is not used yet.

password=value
    Set the password value, needed with the login for authenticated mode. This feature is not used yet.

IMPLEMENTATION
The hostname of the UPS is specified with the "port" value in ups.conf, i.e.:
	[mgexml]
		driver = netxml-ups
		port = http://netxml-ups.example.com:80
Specifying the method how to connect to the UPS (http, https) is mandatory. If the port is equal to the default for the method specified (80 for http, 443 for https) it may be omitted. In order not to overload older NMCs by polling them too frequently, it is recommended to increase the "pollinterval" (see nutupsdrv(8)) and ups.conf(5)) to at least 5 seconds.

KNOWN ISSUES
Don't connect to the UPS through a proxy. Although it would be trivial to add support for proxies, this is not recommended and don't ask for it. Not only because it will prevent the driver to make a persistent connection to the UPS, but also it adds an additional failure mode. If the proxy goes down (for whatever reason), the driver will no longer be able to reach the UPS.

AUTHORS
Arjen de Korte <adkorte-guest@alioth.debian.org>

SEE ALSO

  The core driver:
nutupsdrv(8)

  Internet resources:
The NUT (Network UPS Tools) home page: http://www.networkupstools.org/